Satisfied with installation.
Lennox ac....low charge
Complete 1 system 3 presons Carier AC, perform EPA cooling maintenance. Checked thermostat and air filter. Checked blower motor amp draw. Checked all wiring. Checked run cap. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned condenser coil. System is running great at this time.
Nordyne duel fuel package unit. Repaired low voltage wire
Nordyne straight a.c. Replaced bad capacitor
Carrier split system Heat Pump
Carrie gaspack no issues
Goodman hp repair
Goodman hp check
Goodman Heat Pump
Carrier heat pump checked system found bad contactor and replaced and cycled system working at this time
Complete one system, downstairs system. Preformed heating maintenance and found no mechanical issues. System is operating properly at this time.
Carrier no ac leaking coil