Satisfied with installation.
Nordyne duel fuel package unit. Repaired low voltage wire
Nordyne straight a.c. Replaced bad capacitor
Carrier split system Heat Pump
Carrie gaspack no issues
Goodman hp repair
Goodman hp check
Goodman Heat Pump
Carrier heat pump checked system found bad contactor and replaced and cycled system working at this time
Complete one system, downstairs system. Preformed heating maintenance and found no mechanical issues. System is operating properly at this time.
Carrier no ac leaking coil
Lennox replace zone control board
Complete. Found clogged drain line, cleared out. System is operating properly at this time.