I love the way he explained everything so I would know what to expect, what was happening and why. Attention to detail was evident. When confronted with a problem, it was visible he was thinking in through and when he couldn’t, he didn’t try to BS his way out of it, he asked for help. That is honesty and transparency. Love it!
Men worked quickly and effectively
Amanna heat pump completed cooling maintenance and cycled system working at this time
Trane heat pump and Amanna A/C and Amanna heat pump completed cooling maintenance and cycled system working at this time
Amana Heat Pump
Lennox hear pump checked system found CFM not running due to bad dual run capacitor and replaced and cycled system working at this time
Complete 1 System Amana Straight A/C: Checked thermostat and air filters. Checked blower motor amp draws. Checked all wiring. Inspected evap coil and blower wheel. Checked run cap. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked dual cap. Found it way too weak. Talked to HO about it. She requested to get cap replaced. Replaced it with 35/5Uf. Used new one from truck stock. Old one was rusted out. Couldnt see size. Had to search it out.Cleaned condenser coil. Checked pressures. System is running great at this time.
Carrier gas pack need to pull blower motor and checked heat exchanger due to open roll out switch unable to due to due to rain
ICP heat pump checked system found bad defrost contral board need to replace contral board
Ruud package heat pump checked system found thermostat programed wrong and reprogrammed thermostat and cycled system working at this time
Complete 2 System worked on Main Unit Carrier HP Split System. HO stated system was not working properly. Found bad thermostat. Replaced it. Sysyem is running great at thi time
Carrier heat pump checked system found to be working at this time
Working on a Lennox package heat pump
Mini split no heat