Good men equipment blown 35 5 dual capacitor second floor
Nordyne AC not cooling
Amanna heat pump replaced ECM motor and cycled system working at this time
Amanna package heat pump completed cooling maintenance on system and cycled system working properly at this time
Amanna heat pump completed EPA cooling maintenance and cycled system working at this time
Heating maintenance on a rheem heat pump
Heating maintenance on gaspack and co electronic check.
Ruud heat pump checked system found open high pressuer swtich and reset and found high refrigerant pressures and adjusted superheat and cycled system working at this time
Heating maintenance on a Goodman heat pump
Heating maintenance on a Goodman gas pack
Heating maintenance on a nordyne heat pump
Trane gas pack
Honeywell standby 22kw generator installation.
Repaired Bryant split system by replacing the condenser fan motor and capacitor