Men worked quickly and effectively
Complete one system. Found compressor and cfm not running due to bad dual capacitor and burnt wire going to capacitor. Replaced capacitor and repaired wire. System operating properly at this time.
Trane... blown 40/5 capacitor
Hail heat pump checked system found to be low in refrigerant and added 1 lb R-22 and cycled systems working at this time
Amanna heat pump completed coolong maintenance system and cycled systems working at this time
Ceckin duct work??
Amana split system
Amana hp....cooling tune up
Intertherm mobile home....replace blower motor wheel
Trane gas pack.....heating tune up
Goodman Split system Heat Pump
Amanna heat pump completed heating maintenance and cycled system working at this time
Trane furnace check
Carrier gas pack repair