They was a great team they worked hard all day to get the job done, they had already been here about 7 hours but the system wanted to act up after they tried the heat and cool but they was not leaving until they was up and running good
Heil gas pack checked system found low suction and high head due to stopped up cap tubs and distributor on evap coil need to replace evap coil
Worked on Comfortmaker heat pump
Complete one system. Found blown 3 amp fuse replaced failed thermostat. Checked charge. System is operating properly at this time.
Changed mobile home furnace, mortex coil, and heat pump.
Lennox no ac
Trane Heat pump
Armstrong heat pump checked system found very dirty air filter and removed and adjusted super heat and sub cooling and cycled system working at this time
Armstrong heat pump replaced out door TXV and biflow drier and recharged system with 10 lb R-410 and cycled system working at this time
Lennoxe heat pump replaced high and low pressure switches and cycled system working at this time collected 0
Lennox no heat
Carrier gas pack Sanyo mini-split bonus room unit gas Pack 1 lb low mini split cooling properly