Very informative presentation for whole house Generatir. Got the work done quickly & told me what they were doing each step of the way. Answered all my questions in a way that I understood the entire process!
We have had to see them more than I would like this summer, but they are always responsive, courteous, and kind.
This company was awesome from the very beginning! We work full time weekly careers & we were not the easiest client to schedule. I highly recommend Comfort Air of Sanford. We are grateful ‘
Rennea is very professional and helped me twice now with getting a new unit
Complete: 1 System EPA Maintenance: Goodman Str8 AC GAS Furnace: Furnace: Checked the Amp Draws on the blower motor. Checked the capacitor. Checked Heat Exchanger. Cleaned burners, Flame sensor and Checked Roll out switch. Checked amp draws on inducer motor and Cleaned it out. System looks good and working good at this time.
Complete one system, Lennox heat pump. Preformed heating maintenance cleaned coils, checked charger, parts, amp draws, and heat kit. System is heating properly at this time.
Working on a Goodman heat pump
Working on a Trane heat pump
Working on a Goodman heat pump
Complete one unit, whole house Trane straight a/c. Found secondary pan full of water due to clogged drain line. Replaced the p-trap and blew out drain line. System is operating properly at this time.
Install 20 kw Briggs & Stratton Fortress whole home generator
Working on 2 Lennox A/C systems
Complete one system, main heat pump. Found bad contactor and replaced it. System is operating properly at this time.
Complete one Carrier heat pump. Found bad capacitor and replaced it. System operating properly at this time.
Complete one Carrier heat pump. Found bad capacitor for the compressor and replaced it. System is operating properly at this time.
Complete: Rheem Package unit: HO said she likes it at 69 during the day and it only stays around 71-72. We completely washed the unit inside and out and checked charge. Looks like a new system. Told her not to call us back (I really did but had her laughing) told her that the system will not be able to stay at 69 during the heat of the day that she will need to bring the temp up. She says she completely understands and will not call us back. Unless of course it stops. :) ...... system working great at this time.
Complete: 2 systems worked DS Unit Ameristar split HP: Replaced HPC and board came out of lock out. Pressures looked a little low but the system has been off for two weeks and my temp split was good. System working great at this time. I did not collect bc HO showed me a receipt where he had prepaid. Called and confirmed that.
Complete: 3 systems worked on All 3 Goodman split HPs. HO said none of the systems were maintaining temp. The Basement system found a bad cap. Changed Cap and system came on checked charge and working great at this time. Main Floor system found system frozen up but not bad so quick de-ice and added 2lbs of r22. System is working great at this time. Top floor system I believe it was struggling bc the both bottom floor units weren’t working. But checked charge and components and all looked good at this time.
Complete: 2 systems worked on DS Unit Amana Split HP: Replaced condensate pump, removed 2 kinks and blew out tubing. Rewired float switch back into system. Tested condensate pump and it works. HO had ran an extension cord to run condensate pump. The outlet under house is still not working. System is working great at this time!