I will always recommend your company First and foremost to all our friends and family
They were fast and efficient. They really knew their job
Super nice, well informed and extremely helpful! Great guy
The technician (BJ) was very informative, very professional and knowledgeable
We had to reschedule
Michael went the extra mile to help get our AC back up and running. He was thorough in his service, checking the AC unit, air handler before ensuring the air vent output temperature was in the acceptable range.
Complete: 2 Systems: EPA Maintenance Amana Split Heat Pump: Air Handler: Checked Amp Draws on the Blower Motor and Heat strips, checked the blower wheel. Inspected Evap coil. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. System looks good and running Great at this time.
Amana split heat pump maintance
EPA on a Amana heat pump system
Working on a Goodman heat pump
Complete: 2 systems worked on US Unit: Goodman Split HP: HO said was blowing but not cool or hot air. Found condenser not coming on. Found capacitor completely dead. Changed capacitor, checked amp draws and charge. Also found O wire not energizing in cool mode. Checked at AH to see if there was 24v on the O wire being it was a vivant Tstat on the wall and there was none. Bad tsat. HO is going to call Vivant to Change out Tstat. Units need to be maintained as well left HO info for maintenance.
Working on trane heat pump.
EPA maintenance on a Goodman heat pump system
Amana split heat pump no heat
Western house Heat Pump
Working on goodman heat pump
Carrier Heat Pump
Carrier HP split replaced defrost board
Nordyne heat pump heating maintenance