My overall experience with Comfort First A/C has been excellent! The two technicians were quick and responsive to questions.
Expert friendly service
Complete: two systems: worked on upstairs system: Goodman, split heat pump: king to change out evaporator coil. Pulled old evap Installed new one replaced P-trap, pressurize system, no leaks. Pulled vacuum added 9 pounds of r22. Delta T 18 degrees. Recommended SH 11 when I left it was at 18 and dropping. System looks good and running great at this time
Goodman split heatpump no cooling
Working on a Goodman heat pump
Diagnosed bad thermostat
Replacing service valves on a Goodman heat pump
Replaced condensate pump on a Trane heat pump
Upstairs Unit: Goodman Split Heat Pump: Air Handler: Checked Thermostat and Capacitor, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Very tight Ptrap, cleaned out. Added pan tabs to primary and checked condensate line. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils System looks good and running Great at this time.
Complete: Trane Split heat pump: came to switch out fan motor. Wired fan motor up replaced with a new Capacitor. Went under the home and strapped up main duct line in five locations with tape and metal strip. Had Homeowner turn system on to check vents and cooling and everything is working
Replaced customer provided air filter on Goodman heat pump.
Replaced bad capacitor on a Goodman heat pump
Performed leak search on Bryan heat pump
Working on a Lennox Heat Pump
Working on goodman heatpumps.
Carrier split heat pump no heat
Diagnosing Payne Gas Pack unit. Found blower wasn’t working. Tested capacitor and found it needed replacing. Replaced the capacitor and that fixed the issue. Unit is running great.