Upstairs Unit: Goodman Split Heat Pump: Air Handler: Checked Thermostat and Capacitor, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Very tight Ptrap, cleaned out. Added pan tabs to primary and checked condensate line. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils System looks good and running Great at this time.
Complete: Trane Split heat pump: came to switch out fan motor. Wired fan motor up replaced with a new Capacitor. Went under the home and strapped up main duct line in five locations with tape and metal strip. Had Homeowner turn system on to check vents and cooling and everything is working
Replaced customer provided air filter on Goodman heat pump.
Replaced bad capacitor on a Goodman heat pump
Performed leak search on Bryan heat pump
Working on a Lennox Heat Pump
Working on goodman heatpumps.
Carrier split heat pump no heat
Diagnosing Payne Gas Pack unit. Found blower wasn’t working. Tested capacitor and found it needed replacing. Replaced the capacitor and that fixed the issue. Unit is running great.
Goodman split HP cond
Cleared drain line on Goodman heat pump
Working on a nordyne heat pump
Providing an estimate to replace 2 split heat pumps (Goodman and trane) with 2 Amana split heat pumps.
Performed diagnostic on Goodman heat pump
Working on a Goodman heat pump