Carl came to my house within 3 hours of me contacting their office. Was very thoughtful putting shoe covers in before coming in asked a lot of questions before starting to get best idea of what was going on. Could have easily sold me on replacing as much as they wanted to but he gave me a basic run down of the situation asked what I thought and was made part of the process versus being told what to do. Carl was efficient with his time and had the issue resolved in less than 30 minutes. Now our HVAC unit is as good as new. Thank you Carl and the Comfort First Team!!!!
Kelli seems very personable and understands our current situation. It was a pleasure working with her.
Goodman AC second 2 lb slow R22
Trane equipment no AC first floor safety switch head system out stop drain line
Repaired a Goodman heat pump by replacing the capacitor
Cooling maintenance on 2 Goodman heat pumps
Diagnosed a bad heart exchanger on a Goodman gas pack
Trane gas furnace replaced fas valve and cycled system working at this time
Amanna gas pack and Amanna heat pump completed EPA cooling maintenance on system working properly at this time
Diagnosed a bad gas valve on a trane gas furnace
Repaired Goodman package unit by replacing inducer motor
Replaced coil in a Goodman split system