Had a new heat pump installed today and the service I received was great. These are a great group of guys. Top notch from start to finish. Thanks
Very professional and very know
I was able to talk over the problem with the service manager, the techs were very interactive and got the job done right and in a timely manner! A+!
Train package unit found fallen Duckworth
Incomplete 1 System Goodman Pak System: HO were out of town. Dogs babysitter said she knew about us coming to check A/C, but she didnt know any thing about retail diagnostic feed or any repaire expenses. Called HO, didnt answere. Called tech support. They told me they called HO and left message. Started timer. Will need to reschedule.
Incomplete 1 System 2 Zones Goodman HP Split System: HO stated system was not cooling. Found system at the evap coil frozen. Will need to reschedule. Pics under docs.
Complete 1 System Payne HP Split System. HO stated system was not cooling. Found bad dual cap. Used a 45/7.5 dual cap from truck stock. Checked pressures. System is running great at this time.
Complete 1 System Nortech HP Split System. Replaced fan control board. Tested. System is runnin great at this time.
Complete 2 Systems worked on DS Payne HP Pak System. HO stated system was not cooling. Found bad dual cap. Used a 35/5 cap from truck stock. Checked pressures. System is running great at this time.
Working on a Carrier package unit
Carrier cooling maintenance
Complete: 1System Payne Split HP with old AH. HO said that “system is on and running and set to 68 but it’s not getting cold in here.” Went outside and system was trying to run and very hot to the touch but had a bad 70/5 cap. Changed cap system came on and running as it should at this time.
Complete 1 Pak Unit HP A/C: Checked thermostat and air filter. Checked blower motor amp draw. Checked all wiring. Checked run cap. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned condenser coil. System is running great at this time.
Trane split straight a.c. secured blower door correctly
Norydne heat pump checked system found grounded compressor
Ruud split heatpump preformed cooling maintenance
Amana split heatpump preformed cooling maintenance