Very professional and very know
I was able to talk over the problem with the service manager, the techs were very interactive and got the job done right and in a timely manner! A+!
Complete one repair, Goodman gas pack. Found blown capacitor and replaced it with 45/5 capacitor. System is operating properly at this time.
Goodman split heat pump. Replaced leaking evaporator coil and recharged system
Complete: 2 systems worked on US unit: Trane split HP: HO said once he changed the breaker the system worked for a couple days and quit. We checked the HP and found bad cap. Changed 25/5 cap and system came on. We checked the pressures and system is working great at this time.
Amanda heat pump adjusted super heast and cycled system working at this time
Goodman cased coil
Checked goodman split system heatpump for upstairs
Amanna heat pump checked system found safety tee tripped in drain line due to stopped up primary drain line and cleared and cycled system working at this time
Goodman split heat pump Diagnosed leaking evaporator coil
6 system EPA cooling maintenance 2 gas pack 4 split system heatpump rheems
Goodman split heat pump. Reset popped gfi for condensate pump
Goodman heat pump added Hard Start to help compressor
Trane split heat pump. Fixed wiring on thermostat
One Carrier split system heat pump. Found bad fan motor.
Bad defrost board on Bryant split system heatpump
Covenantial EPA cooling maintenance on Goodman split system with gas furnace