Had a new heat pump installed today and the service I received was great. These are a great group of guys. Top notch from start to finish. Thanks
Very professional and very know
I was able to talk over the problem with the service manager, the techs were very interactive and got the job done right and in a timely manner! A+!
Goodman air handle replaced zone damper motor and zone contral board and cycled system working at this time
Carrier heat pump checked system found defrost sencer not properly mounted and repired and cycled system working at this time
Goodman gas pack repaired dented duct shroud
Amana split heat pump 3 zone. Reprogrammed thermostat after power outage
Carrier gas package unit. Replaced heat exchanger and flue cover
Goodman split heat pump Added refrigerant
Goodman split heat pump. Diagnosed leaking evaporator coil
Goodman split heat pump 3 zone. Diagnosed bad zone damper motor and control board
Goodman split heatpump found bad zone board and zone damper
Goodman hp no heat...no power on home
Complete 2 System worked on DS Tempsar dual fuel system came to replace compressor. Replaced old compressor added refrigerant. Checked pressures system is running great at this time.
Ruud split heatpump changed thermostat
3.5 ton heat pump change out. Goodman 14 seer
Complete: 1System EPA Maintenance: Trane Str8 AC GAS Furnace: US Furnace: Checked the Amp Draws on the blower motor. Checked the capacitor. Checked Heat Exchanger. Cleaned burners, Flame sensor and Checked Roll out switch. Cleaned it out. System looks good and working good at this time.
Blower motor capacitor