Complete 1 System Goodman Gas Furnace Syraight A/C System came to perform EPA Cooling Maintenance. Checked thermostat and air filter. Checked blower motor amp draw. Checked run cap. Found it out of its range. HO said he will wait until it goes bad. Checked all wiring. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Found it out of its range. HO also said he will wait until goes bad. Checked pressures. Cleaned condenser coil. System is running great at this time.