Ben is polite and provides incredible service. He represents your company well.
Replaced heat kit on a Trane air handler
Working on a Trane heat pump
Complete: 1 Systems: HSA Maintenance Rheem Split Heat Pump: Air Handler: Checked Amp Draws on the Blower Motor and Heat strips, checked the capacitor and blower wheel. Inspected Evap coil. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. System looks good and running Great at this time.
Replaced compressor on Goodman heat pump system
Complete: EPA Maintenance: Trane Split Heat Pump: Air Handler: Checked Thermostat and Capacitor, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Replaced P-Trap, checked condensate line. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils System looks good and running Great at this time.
Performed preventive maintenance on trane heat pump.
Added r22 refrigerant to Goodman heat pump
Performed preventive maintenance on trane heat pump
Complete: 1 System American Standard: HO complained of knocking sound through out the night and when it gets really cold. Found when we turned on the Gas Furnace that the gas line running into the unit would vibrate against the housing as well as up on one of the floor joist. Placed Armor Flex around pipe in both locations and that seemed to fix the problem.
Routine maintenance on a Goodman heat pump
We are installing a new Amana split heat pump with a newly designed duct system to provide better airflow.
Repaired a Goodman heat pump by replacing the compressor and setting to correct charge
Diagnosed a bad compressor on a Bryant heat pump
Carrier split heat pump no heating
Working on a york heat pump