Ben was awesome. Timely, professional, efficient.
Ben is polite and provides incredible service. He represents your company well.
Complete two systems, worked on downstairs, Trane heat pump. Found bad duel capacitor and replaced it. System is operating properly at this time.
Routine maintenance on an Amana heat pump
Complete one system, Trane heat pump, two zones. Found loose wire at the air handler and fixed it. System is operating properly at this time.
Complete: 3 systems worked on Bedroom Trane split Hp. Came to run Tstat wire from soffit to unit to be uniformed. Also added new start assist and start assist relay. Used 6-10ft of water tight conduit. System is working great at this time. Also spoke with HO about 3 system maintenance plan. Gave him paper work.
Cleaned a drain line and pan on a Carrier heat pump
Trane split Heat pump
Complete 2 systems worked US unit: Goodman split HP: HO said stopped cooling yesterday but since came back on. Checked condensate line and it was stopped up. Cleaned out line replaced Ptrap and water is draining great at this time.
Complete: 2 systems worked on DS. HO was concerned with temp not meeting Tstat. Found system seemingly a little over charge. Just adjusted a little best I could get at the AH was a 15° split. 48 degree supply air. Everything seems to be working as good as the system can give for its age. She’s trying to keep temp at 67-68 at night. I told her she needs to keep it if possible between 71/73 at night if possible. System is working as it should at this time.
Incomplete: 1System EPA Maintenance Trane Split HP Complete: 1 System: EPA Maintenance Goodman Split Heat Pump: Air Handler: Checked Thermostat and Capacitor, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Replaced P-Trap, checked condensate line. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils System looks good and running Great at this time.
Trane heat pump cooling maintenance
Complete: 2 systems worked on US System: Heil Split HP: HO said was leaking water in the attic ceiling. She also said that the last people who came out told them what to look for and what to do to remedy. Ok Sound i found in attic AH that yes, the pan was full, but several issues. 1. Bad Float switch, 2. Primary condensate line had a backwards pitch due to some tile shoved under it. 3. The door cap that covers the Evap condensate was left on over top of the existing one which didn’t allow the male pvc to be tightly screwed in. 4. Clogged secondary line. ...... Replaced Float switch, replaced Ptrap and solved pitch issue. Also blew out secondary. Now there is still a lot of rust in that pan as well as in the primary pan. Informed HO of all findings. I also used pan tabs in the primary. System is working as it should at this time.
Working on a Carrier heat pump
Complete: Finished EPA maintenance on US system. Checked Amp draws and charge on unit. All is looking good at this time.
Complete: 2 systems worked on US Unit: Heil split HP: Came to replace warranty coil. Changed filter dryer, ran nitrogen, Hot Very Tight Attic, removed old Evap and installed new one. Pulled vacuum, no leaks, added 8lbs of 410. SH and SC were spot on. Delta T was 16 degrees it was 84 degrees in the house. Unit is working great at this time.
Complete: 2 systems worked on DS Unit Heil split HP: Came to replace blower control board. Replaced board and system came on as it should. Then unit cut off. Found condensate line stopped up and condensate pump would no longer pump. Blew out line and replaced condensate pump. Checked charge really hot in the house. Charge looked great. 20degree delta T and 12degree SC. Unit is working great at this time.