Billy did a great job explaining what was wrong with my air conditioning unit and even listed options that could be done and the outcomes of each option. Thanks.
Trane A/C checked system found bad condenser fan motor
Trane and Amanna A/C completed EPA cooling maintenance and also completed minor duct repaor and cycled system working at this time
Goodman gas packed checked system found rusted thought heat exchanger need to replace heat exchanger
Worked on Goodman heat pump
Complete one system gas furnace. Did bubble spray all joints, found leak at drip leg. Took drip leg off resealed and put back on. Found no other leaks at this time.
Complete one system check. System operating properly at this time.
Worked on Goodman air conditioner
Worked on Carrier Air Conditioner
Trane A/C with case coil checked system found float swtich tripped in condensation pump casing system to cut down due to tripped GFCI outlet and reset outlet amd cycled cycled system working at this
Carrier ac check
Rheem gas pack
Goodman ac check
Goodman AC unit.