Billy did a great job explaining what was wrong with my air conditioning unit and even listed options that could be done and the outcomes of each option. Thanks.
Complete one system gas furnace. Did bubble spray all joints, found leak at drip leg. Took drip leg off resealed and put back on. Found no other leaks at this time.
Complete one system check. System operating properly at this time.
Worked on Goodman air conditioner
Worked on Carrier Air Conditioner
Trane A/C with case coil checked system found float swtich tripped in condensation pump casing system to cut down due to tripped GFCI outlet and reset outlet amd cycled cycled system working at this
Carrier ac check
Rheem gas pack
Goodman ac check
Goodman AC unit.
Trane equipment replace cfm
Goodman heat pump checked system found open low pressure switch due to being low in refrigerant and preferred leak search and found leaking evap coil need to replace evap coil
Carrier no ac
Comfortmaker 90% gas furnace checked system found open pressure switch due to draft inducer motor not running due to being bad need to replace draft inducer assembly