Routine maintenance on Trane heat pump
Working on a Goodman gas pack
Lennox furnace replaced pressure switch and blower motor capacitor
Rheem heat pump not heating
Goodman furnace replaced control board and Highlimit switch switch
Trane gas pack replaced outdoor TXV
Goodman gas furnace Diagnosed bad control board and limit switch
Trane package heat pump. Fix refrigerant leak and diagnosed bad txv
Goodman heat pump package unit diagnosed bad blower motor capacitor and replaced everything working
Working on goodman heat pump.
Carrier Bryant equipment heat check
Carrier AC blowing dual capacitor
Trane equipment no issues second floor safety switch stuck
Replaced compressor.capacitor.added refrigerant.on Goodman unit.check charge.operation good !
Goodman a/c bad compressor R22 refrigerant