Owning a reliable, safe system is at the top of our list for comfort and healthy environment
Westinghouse package unit no heat capacitor 7.5
Complete 1 System Trane HP Pak Unit. Performed EPA Heating Maintenance Checked thermostat and air filter. Checked amp draws on heat strips and blower motor. Inspected evap coil. Made sure drain line was clear. Checked compressor and cfm amp draws. Tested defrost board. Checked dual cap. Checked pressures. Cleaned condenser coil. Checked all wiring. System is running great at this time.
Carrier split straight acnwith gas furnace. Replaced faulty thermostat and checked system for proper operation
Complete two systems up. Found cfm not running and bad dual capacitor. Replaced capacitor and cfm started. System operating properly at this time.
Carrier Heat pump found bad evaporator coil
Carrier hp...inter....no ac
Lennox equipment...zone damper motor bad
Carrier hp.....no cooling drains stopped up
Carrier ac.1bl low r22
Trane package heat pump. Cooling maintenance
Checked coleman 2 zone split system straight ac
EPA cooling maintenance
Installed Honeywell zone board