Owning a reliable, safe system is at the top of our list for comfort and healthy environment
Complete two systems up. Found cfm not running and bad dual capacitor. Replaced capacitor and cfm started. System operating properly at this time.
Carrier Heat pump found bad evaporator coil
Carrier hp...inter....no ac
Lennox equipment...zone damper motor bad
Carrier hp.....no cooling drains stopped up
Carrier ac.1bl low r22
Trane package heat pump. Cooling maintenance
Checked coleman 2 zone split system straight ac
EPA cooling maintenance
Installed Honeywell zone board
2 epa cooling maintenance on 2 amana split system heatpump
Just finished installing a 2.5 ton Amana 16 seer split heat pump and Premium Duct System. Also installed a Nest learning thermostat.
Routine maintenance on Trane heat pump