Real good service
Owning a reliable, safe system is at the top of our list for comfort and healthy environment
Complete 2 Systems worked on US Trane HP Split System 2 Zones. Replaced condenser hard start kit. Tested. System is running greatnat this time.
Complete 2 Systems worked on DS Carrier HP Split System. HO stated suction line was freezing up affer 4 mins of running. Cycled system, let it run for about 10 mins. Pressures were right. Checked compressor, cfm and blower motor amp draws. Checked dual and run caps. Inspected evap coil. Air filter was clean. Made sure heat strips were not coming on. Couldnt find any thing wrong with system. System is running great at this time.
Working on a Payne heat pump
Working on a Trane A/C system
Goodman case coil checked system found bad TXV need to replace
Duct system checked duct found sevral duct pulled out of duct that can not berepaired
Complete: 1System Amana split HP: HO said was on last night but got up to 86°. When I arrived the system had satisfied at 72°. I went under the house which isn’t sealed but there was heavy condensation on everything even inside the cabinet. Shut system down and adjusted speed tap to high speed. Cut system back on and blower didn’t come on. I was testing voltage and found only 8volts getting through the relay to the fan. Tapped relay with my screw driver and blower came on. Cycled system and it did the same thing. I changed out the relay and cycled the system several times and blower came on
Complete 2 Systems wirked on US Trane A/C: Found bad dual cap and hard start kit. Used 1 45/5 dual cap and new hard start kit from truck stock. Checked pressures. System is running great at this time.
Complete 2 Systems. Worked on Us Goodman Split System. HO said he system was freezing up. Found pressures low. Air filter was dirty removed. Checked all vent to make sure they were blowing. Went to check evap coil to make sure it was clear. Made sure no collapsed flexes. Checked super heat. System was 1 lbs of R22 overcharged. Recovered the 1 lbs of R22. Got a 18 degree super heat. System is running great at this time.
Amana ac check
Trane split system heat pump Replaced fan blower board and blower motor
Incomplete 2 Systems worked on Both Systems, US and DS. US Trane HP Split System: HO just eanted us to make sure system was running properly. Monitored blower motor. Checked air filter and tstat. Monitor compressor and cfm. Checked dual cap. Checked pressures. System is running great at this time. DS Trane HP Split System: HO stated tsat was not responding. Found tstat froze. Tried to reset it, still didn’t work. It was a trane touch screen tstat. Replaced it with a T6 Honeywell tstat from truck stock. Checked pressures. Found system low in ref. Added 2 lbs of 410A, autho. By HO. Let it run for a few mins. Pressures started to drop on suc. Side but head side stayed the same. Went to the AH, found blower motor running at a very low speed which made low pressure go too low. Bad blower motor and board that controls the motor. They both need to be order from D&L, and be replaced. Make sure if it’s not me coming back to replace parts , let the other tech to check pressures agai
3 ton heat pump
Rheem ac check
Nordyne hp repair