Justin was my technician and he was excellent! Very kind and took the time to really explain everything that was being done. He was also on time and very professional.
Billy has an ability that most technicians don’t. He has the ability to share is knowledge of HVAC and explain how things work and don’t. We appreciate his service!
He was excellent. He was knowledgeable and very efficient. We appreciate him.
Excellent Customer Service
Billy was quite efficient and personable. He quickly identified the problem and got me set up to have the issue fixed.
Billy was very professional and did a great job.
Heat Maintenance on 2 ICP gas furnaces
Complete two systems. Worked on upstairs system. Found low in refrigerant and added 1lb of r22. System is operating properly at this time.
Complete one system, main. Found no issues with duct work. Found system low in refrigerant and added 1 lbs of r410a. System is operating properly at this time.
Ac unit not working
Completed two systems, worked on both upstairs and downstairs. Upstairs system, found 35/5 mfd capacitor failed open and replaced. Cleaned condenser coil. Downstairs system, Trane ac split, found dirty condenser coil and cleaned. System operating properly at this time.
Co pressor replacement
Worked on Goodman gas furnace
Work on gas furnace
Compressor on heat pump locked up.
Worked on Lennox gas furnace
Carrier heat pump