Need more like james.
Tech was very knowledgeable and did great job checking the system and detected a major leak on the coil, not just put in freon and call it a day like the last tech did three weeks earlier . I would like to request Billy to be the same to make the repairs on my system. Thanks
pleasant and thorough.
No ac or air flow
Worked on Trane heat pump
Replaced blower control board, float switch, and condensate pump.