Completed ac maintenance with little to no problems for our comfort club member!
Complete ac maintenance. Unit is operating; customer is aware of possible issues.
Completed 2 system ac maintenance
Complete ac maintenance. Replaced contactor; all is operating properly.
Completed ac start up and ac maintenance
Serviced and repaired a 20yr old york furnace
Complete boiler maintenance on Burnham. All is operating properly at this time.
Maintenance on a Carrier furnace
Complete furnace maintenance and hum maintenance. All is operating properly. Customer aware of ODT.
Completed two system furnace maintenace, repairs, as well as two humidifier maintenance
Complete a.c. diagnostic. Fan motor needs to be replaced.
Installed a Honeywell wifi thermostat and ran wiring for thermostat
Complete a.c. maintenance
Complete furnace maintenance on Weathermaker by carrier
Complete furnace maintenance on goodman