Shawn was smart, respectful and always on time. Very easy to comunícate with and knee what to do right away. I will use this company in the future, no doubt
ComfortMaster helped us out on a cold Sunday when the furnace broke down. Great service for a new customer.
From meeting Robert, the sales rep, through the installation of my furnace and water heater, I felt Comfort Master was the right provider for me. I found they offered expert and professional service that I can rely on for years to come.
Very clear, polite, competent technician performed our annual maintenance. Answered all our questions.
Being a first time home owner, I felt this was a complete check of all HVAC systems, I learned a lot about how it works.
Burnham Gas Boiler not heating. Found primary control defective and replaced.
Leak from Peerless Boiler heating system, turned out to be coming from humidifier water line. Repaired line and tested operation.
Water heater flue improperly installed under boiler flue. Also found it blocked. Cut into chimney above the boiler flue and closed old openings.
Burnham Gas Boiler and Water Heater Maintenance.
Error code 97 on Fujitsu Ductless. Replaced Main PCB board on outdoor unit. Verified operation after installation.
Rheem Marathon Electric Water Heater Leaking. Found tank defective, and replaced, with Bradford White Water Heater.
New Yorker gas boiler no heat. Found defective burner control and replaced.
Peerless Gas Boiler Clicking on and off. Found defective White Rodgers zone valves on 2 zones. Also performed heating tune up
No heat Utica Gas Boiler. Found pilot not lighting, due to it being wet from water leak at expansion tank. Replaced expansion bladder tank, as well as air vent, and relief valve. Dried pilot assembly and relit pilot, after refilling and purging boiler. Tested for draft and carbon monoxide in flue to chimney.
Tune up on Peerless Gas Boiler.
Replacement of Furnace and A/C with new Amana equipment
AC and Furnace Checkup
Furnace and ac tuneup
York R-22 system not cooling reviewed operation of system and found defective start components reviewed options to resolve