Shawn was great explained everything to me. The quick response to my heating problem was great, happy I am with comfortmasters.
Bob always is professional and very helpful.
Heil AC not cooling. Fan on top of outdoor unit not spinning. Found and replaced defective dual capacitor. Also performed deep cleaning of outdoor unit with high pressure sprayer and cleaning solution
Trane Air XL1200 Conditioning Unit blowing warm air. Found low on freon, and added refrigerant to proper level. Unit is leaking, but due to age, it may be time to consider a new system
No heat on Trane gas furnace reviewed operation and condition of system and found defective door switch
Replaced Flue piping
Old ABS flue pipe on gas furnace leaking, replaced with new PVC flue piping.
Tune up on York gas furnace with Amana A/C coil and condenser.
Crown gas fired boiler has no heat do to defective end switch on zone valve.
Maintenance on gas fired Peerless cast iron boiler.
Replaced type A Suntec oil pump for AFG Beckett burner on EK1 system 2000 boiler.
Amana Gas furnace with ac tune up.
Tune up on Goodman 80% gas furnace with matching A/C coil and condenser.
Furnace and AC System Maintenance
Replaced First Co air handler circuit board.
Replaced First Co circuit board.
No Cooling on 1sr company air handler with Heil condenser do to defective circuit board from extremely plugged filter blocking air flow