Our annual oil burner maintenance visit went well. The Tech was experienced, knowledgeable about our system, friendly, and seemed to do a good job on our old System2000 oil burner in a reasonable amount of time. Thanks
Mike was familiar with the system 2000 boiler. He is the first hvac technician to notice that one of the circulators was not working correctly. He suggested that it should be changed next year.
As always, Bob does an expert job.
We have used Comfort Master for many years now and have never been dissatisfied with the service and response and/or the technicians. We would always recommend them to anyone.
Replaced failed Aquastat with new L7224U Honeywell control on oil fired Burnham V8H boiler
Ductless Heat Pump Maintenance
AC Check Up!!!
Zone valve trouble! No problem!!!
Annual AC Tuneup
Lennox air conditioner not cooling. Found shorted low voltage wire at condenser. Spliced new connection and rewired. Tested operation.
Ac tune up with gas furnace
Ductless mini split tune up and inspection
Oil boiler maintenance and cleaning
Oil furnace with AC tune up
American water heaters. Gas fired natural draft , natural gas hot water heater. Water leak. Emergency service. Emergency replacement. Hot water heater leaking. Gas appliance.
New customer, oil boiler cleaning and system check
Water leak on 40 gal gas fired water heater do to tank failure replaced with Bradford White 40 gal
Furnace making loud noise when operating
Oil boiler tune up and inspection