Corrected issues we had for a long time and they were never addressed properly by past companies we hired.
Great Service - John was professional and informative.
Goodman Air Conditioner with Hydro Hot Water Coil. Installed WiFi thermostat, replaced fan motor. Tested operation of all 3 systems.
Heil AC not cooling properly, thought to be bad txv expansion valve. Found system with airflow issue and overcharged with r410a freon
Tune up on York AC units. 3nd floor not blowing cold, and needed freon charge for proper operation.
Spring tune up of two Amana hydro air conditioners. Rinsed evaporator coils, drain pans, and condensate pump. Blocked air of condensers to simulate warm day, and check operation while still cool outside.
Tune up of Amana A/C and furnace system
Needs Replacement! No AC!!!
Replacement of A/C system with new Amana air handler and condenser.
Ac tune up!
Rinnai Water Heater Install
Amana A/C tune up for optimal efficiency and reliability throughout the cooling season. Clean and flush condensate drain and pump clean condenser and evaporator coils inspect duct work and electrical test refrigerant levels.
First company hydro air handlers with Amana condensers tune ups for optimal efficiency and reliability throughout the season
Annual ac service
Heat pump tune up and seasonal inspection
Replacement of a 3 Ton Amana Variable Speed Attic Air Handler with matching 3 Ton Amana Outdoor Condenser Unit