The Comfort Master team was very efficient, respectful and professional. Sue and Anthony were very professional and efficient in answering my questions and setting up my appointments. Bob, Mitch & Shawn did a great job explaining the process and replacing our whole HVAC system including the ductwork. They also added zoning to the new unit which works out great for us. They were very professional, knowledgeable, and courteous. They took the time to answer our questions and explain the operation of the systems. Not to mention they left the area in impecible condition when they were through. I highly recommend Comfort Master services to anyone who needs HVAC system replacement.
Bob is a great person. He did his job and helped me. And he put in a tank that is going to fix my problem. It’s only the first day. So I will be checking. This is not anything to do with Bob but It hit me and Tina hard
Bob was very professional, thorough and pleasant.
Bob is excellent. What a piece of mind... the dogs barking . I look out the window... YAY it's Bob!. On time, professional, always ensures everything is working properly. Thanks
Robert Monteiro was very polite. He explained what was wrong and how the situation could be fixed so it will not happen again. He was pleasant even though he was called out late at night. He came in a reasonable amount of time.
Performed air conditioning tune up on a Heil condenser and air handler. Rinsed coils and check operation and freon levels. Recommend new compressor contactor and dual capacitor
Ac tune up on a Heil air conditioner. Checked operation. Capacitor and contactor showing signs of age.
No heat on main floor of Peerless oil fired boiler reviewed operation and found broken wire on Honeywell zone valve RE wired and tested operation.
Routine maintenance on Amana gas furnace with air conditioning as well as flushing of Bradford white gas water heater for optimal efficiency and reliability of units.
No hot water from A.O. Smith water heater. Found electrical connections in safety switches to have been disconnected, reconnected and checked thermopile/thermocouple for proper millivolts. All functioning at this time.
Utica Gas Steam Boiler repairs. Added water boiler treatment, installed new steam gauge, pressure control, pressure relief valve, and steam vents in mains and radiators. Also replaced drain valve at bottom of boiler.
System check on Amana gas furnace and A/C
Tune up on Carrier oil furnace with matching Heat Pump and Boch oil water heater.
Malfunctioning control board on Goodman high efficiency condensing furnace.
Tune up on Lennox steam boiler
Tune up on gas fired Burnham boiler with indirect hot water storage tank.
Replace of Gas Furnace and A/C with new Amana 96% Furnace and Amana 16 Seer condenser
Tune up on Amana A/C and gas furnace
Ductless AC Annual Check Up!