Very thorough and extremely knowledgeable; answered all my questions and made for an overall good experience.
They installed my whole Central AC in my house 3 years ago and they were so clean and meticulous. I just had them come and derive my boiler in my home, again excellent job. They even pout on shoe coverings and put down drop cloths . What company does that?
Anthony did a great job. I felt that he did a through examination of the furnace. He pointed out things that no service tech prior to him did. The other techs were in and out in no time. I now wonder how well of a check and cleaning they did. If you can request a tech I will definitely request Anthony next year.
The Comfort Master team was very efficient, respectful and professional. Sue and Anthony were very professional and efficient in answering my questions and setting up my appointments. Bob, Mitch & Shawn did a great job explaining the process and replacing our whole HVAC system including the ductwork. They also added zoning to the new unit which works out great for us. They were very professional, knowledgeable, and courteous. They took the time to answer our questions and explain the operation of the systems. Not to mention they left the area in impecible condition when they were through. I highly recommend Comfort Master services to anyone who needs HVAC system replacement.
Bob is a great person. He did his job and helped me. And he put in a tank that is going to fix my problem. It’s only the first day. So I will be checking. This is not anything to do with Bob but It hit me and Tina hard
Bob was very professional, thorough and pleasant.
Bob is excellent. What a piece of mind... the dogs barking . I look out the window... YAY it's Bob!. On time, professional, always ensures everything is working properly. Thanks
Robert Monteiro was very polite. He explained what was wrong and how the situation could be fixed so it will not happen again. He was pleasant even though he was called out late at night. He came in a reasonable amount of time.
Amana Heatpump System. Performed annual maintenance and tune up. Found condenser coil extremely dirty and performed deep cleaning of coils.
Rheem Gas furnace with ac. Checked freon and performed tune up. Found bad General humidifier valve. Also need to bring box of filters
Heil Air handler in attic, with Heil air conditioning unit outside. Performed annual tune up and check.
York Luxaire Gas Furnace and Air conditioning system 19 yrs old. Tune up of system, many original parts. Budget for repairs and/or replacement of system.
Lennox air conditioning system not blowing as cold as it should due to restricted txv metering device. Also performed annual maintenance
Triangle Tube leaking from low water control. Replaced with OEM part and tested for leaks.
Armstrong Gas Furnace with AC r22 compressor circuit. Performed tuneup and inspection. Heat exchanger rusting but not compromised. Average lifespan of this system is approximately 15 yrs.
Peerless gas boiler with Bradford White Water Heater annual maintenance. Tested expansion tanks, thermocouple and thermopile sensor. Check flue and chimney for blockage and good draft
White Rodgers Thermostats not responding properly to setting. Checked operation but found no issues. Replaced batteries and offered information on what to look for if problem recurs.
Peerless boiler not working sometimes. Replaced customer flue damper and checked operation.
Weil McLain HEII-5 making banging noise when thermostat satisfies. Found noise occurs when manually closing zone valve during pump operation but unable to get boiler to do it on it's own. Swapped zone valve heads with another to see if problem moves to basement zone, or continues on 1st fl zone. Rewired zone valves to proper thermostats and corrected other wire connections.
Gas Steam Boiler annual maintenance tune up. Found muddy sludge in base of boiler from drain valve. Also found nest thermostat powers off when boiler satisfies. Nest batteries may also have battery charging issue due to way its wired.
System 2000 Boiler with Water Heater Maintenance. Found Anode Rod and Scale Stopper needed replacement and changed.
Performed air conditioning tune up on a Heil condenser and air handler. Rinsed coils and check operation and freon levels. Recommend new compressor contactor and dual capacitor
Ac tune up on a Heil air conditioner. Checked operation. Capacitor and contactor showing signs of age.