Carrier Bryant AC not working. Replaced defective capacitor, install new condensate pump and contactor. Repaired low voltage wiring, and leaking vinyl hose. Tested operation.
Lennox cooling system not cooling reviewed operation and found start components defective replaced and tested operation
Amana 16 SEER variable speed air conditioning system tune up for optimal efficiency and reliability throughout the cooling season
Tune up and seasonal inspection of 3 AC units
Oil boiler tune and inspection
Energy Kinetics. System 2000 oil fired boiler. Hydronic heating
System 2000 oil boiler tune up
Peerless oil fired boiler system rejuvenation for optimal efficiency and reliability throughout the heating season
Oil furnace tune up
A/C tune up and Charge
Oil boiler tune up on Energy Kinetics system 2000 boiler with 40 gal domestic hot water storage tank for optimal efficiency and reliability throughout the season
Bled oil lines on furnace that ran out of fuel
Diagnosing a broken air conditioning system, mini split r410a
Oil burner maintenance
Replaced Amana Air Conditioning Condenser & Evaporator Coil onto existing Oil Furnace after it was hit by lightning.