He patiently answered my questions and analyzed the problem and explained the solution, and the job he’s going to do.
Had an issue with my air. Called cool air solutions and Luke responded. Absolutely wonderful. Fixed the issue an went over my new equipment with me til I understood.
Very satisfactory experience. Took his time to explain and was very knowledge on the produce.
Client stated no heating -Flame would ignite for a split second and then shut off when power from thermostat -Furnace cuts out on high limit after 10 minutes -Temp rise is good -Return intake is 16â€ but gets reduced down into a very small return grill (14x20) -There is not enough airflow being drawn from house to properly cool the heat exchanger -A new return needs to be cut in to increase intake cfms
Door switch was installed, system is properly working<br> -Flame sensor cleaned<br> -Filter replaced<br> -Proper resistance for components <br> -Amps on motor is good
Technician arrived to perform furnace tune up -Filter is still clean -Flame sensor cleaned off -Electrical connections tightened -Heating elements working properly -Gas piping does not have sediment trap, was recommended -Blower motor is in rough condition, it is very dirty a drawing more power than it should -Blower motor replacement was also recommended -Clients are interested in repairs, would like me to follow up on February 3rd, after the holidays
Flue vent was in very bad condition and not safe to run the heater -New flue venting for furnace was installed, from bottom to top -Venting on roof was sealed properly to ensure no water leaks -Filter was extremely dirty, it was removed, tenant said he will replace it -Flame sensor was also cleaned off -Heating was ran for 30+ minutes, everything is working properly -House has good air flow
Performed a heating maintenance on a 2017 Goodman system. Cleaned and Adjust Burners. Check Combustion Air for Proper Venting. Examine the Heat Exchanger for Damage / Corrosion. Test Furnace Safety Controls. Inspect Gas Piping. Tighten Electrical Connections. Measure the Voltage and Amperage. Flush the Condensate Drains. Measure Tempurature Difference between Supply and Return Air. Vacuum Furnace Return Grille. Adjust Gas Pressure & Pilot. Clean in-place Blower Compartment. Inspect Blower Wheel for Proper Balance. Check the System's Static Pressures to Ensure Proper Airflow. Inspect Duct Connections for Air Leaks / Sizing / Insulation. Check all System Safety and Limit Switches. Clean Flame Sensor. Inspect Carbon Monoxide Detector. Check Thermostat for Proper Operation / Calibration. Filters where changed this visit.
During my twenty point heating inspection, I started with the thermostat. Giving a call for heating, and going to furnace to start maintenance. I checked out blower motor of any dirt or debris and itâ€™s dirty. Both blower motors on each system should be deep cleaned. Dirt has built up on wheel fins. Motor controls are in good standing for both systems. Evaporator coil is starting to deteriorate on both systems. Starting to fall off during maintenance cleaning. One of the compressors for smoke shop is failing. Exceeds past 30 amps and decides to shut off after running for hour. I did last maintenance inspection, in beginning of year and this was same issue I addressed. Lots of amps are being used while running systems.
Upon arrival performed diagnostic, client has a bad thermostat. System kicks on when I jump at thermostat. Last set of fuses were blown. But passed technician said there was a ton of things that needed to be replaced. Client replaced there old thermostat because the screen wouldnâ€™t kick on anymore. New thermostat was not programmed to heat pump. Programmed and system still didnâ€™t run. Thermostat is not fully communicating to system. Bad thermostat. System is non operational. Also had disconnect in backwards so at first was never receiving power. Client is gonna return current thermostat . Please bill commercial owner
Arrived at Commercial building and started with unit on right side. Killed power to unit and started checking motor controls. System has a single motor control which was reading a little low, and the dual motor control that was reading low. I then checked out contactor and contacts were black and pitted. Contactor needs replacing too, blower motor (good), mother board (good), 24v (good), 240v (good). Coil cleaned and brushed to get dirt out of coil. Made sure pvc pipes were cleared and no back up drainage. Condenser fan motor is exceeding max amps, fan motor will fail. Condenser fan motor needing to be replaced. Compressor is exceeding max amps and will soon fail. Compressor using 20 amps and limit is 19.4. I recommended replacing whole package unit, because replacing all the parts internally will not fix compressor issue. Compressor is heart of system, system was low refrigerant of R22. There may be a leak in system, my pressures were really low on the low side. There is piping freezi
Installed PBA control board and programmed system in test mode. Installed outdoor surge protector.
Diagnosed defective board on outdoor Samsung system. Confirmed with tech support. Ordered replacement part with and will be installing with surge protector on the disconnect box.
Arrived on site performed maintenance on 18-year-old American standard. Checked the 55+5 capacitor and itâ€™s within limits. Did deep cleaning of condenser coil fins. Temperature split was within 20Â° refrigerant pressures were in range. Although system did contain R22 which is no longer manufactured as of 2022. Checked filter which was clean. Upon departure system was operational.
Arrived on site to perform spring tune up on Goodman 2017 unit. Condenser located in back yard. Furnace located in attic. Tenant Staters no issues. Washed condenser coil inside and out. Primary starter is good. Secondary motor control is good and in range. Fan motor is good and amps are in range. Checked start up amps on compressor and are good and run amps as well. Checked refrigerant pressures and unit is holding charge and cooling hole at 20 degrees. No protection on unit and recommended adding some. Found filter dirty and replaced. Tenant paid for filter. Blower wheel is good. All safety switches are operational. Drain lines are dirty but still draining. Advised no protection on unit and recommended protection to protect systems from electrical surges and power outages that can damage or even short out systems and components. Called owner and she is aware of how unit is running and recommendations. Client did want to go for with adding protection on both units. Installed surge pro
This is the estimate for both the Main System and the Addition System. Additional Options: - Downgrade to a basic single-stage outdoor and a single-stage indoor unit for the main house: -$2,150 - Upgrade the efficiency of the Addition's condenser to 18 SEER and increased capacity for future expansion: +$600 - Zoning for the main house: +$3,800