Had an issue with my air. Called cool air solutions and Luke responded. Absolutely wonderful. Fixed the issue an went over my new equipment with me til I understood.
Very satisfactory experience. Took his time to explain and was very knowledge on the produce.
Arrived on site to perform spring tune up on Goodman 2017 unit. Condenser located in back yard. Furnace located in attic. Tenant Staters no issues. Washed condenser coil inside and out. Primary starter is good. Secondary motor control is good and in range. Fan motor is good and amps are in range. Checked start up amps on compressor and are good and run amps as well. Checked refrigerant pressures and unit is holding charge and cooling hole at 20 degrees. No protection on unit and recommended adding some. Found filter dirty and replaced. Tenant paid for filter. Blower wheel is good. All safety switches are operational. Drain lines are dirty but still draining. Advised no protection on unit and recommended protection to protect systems from electrical surges and power outages that can damage or even short out systems and components. Called owner and she is aware of how unit is running and recommendations. Client did want to go for with adding protection on both units. Installed surge pro
Remainder of the original install
This is the estimate for both the Main System and the Addition System. Additional Options: - Downgrade to a basic single-stage outdoor and a single-stage indoor unit for the main house: -$2,150 - Upgrade the efficiency of the Addition's condenser to 18 SEER and increased capacity for future expansion: +$600 - Zoning for the main house: +$3,800
Performed furnace maintenance on 2004 American standard heater. Upon arrival homeowner stated that system has been working fine and seems to be working even better since we had install the thermostat last visit. Perform safety inspection and maintenance on heater 1. Found that system is not equipped with surge protection in the case of a power outage 2. Flame sensor is in bad condition although was cleaned off at this time recommend that this is replaced to prevent future failure 3. Indoor blower motor was heavily caked woth dust and debris due to washable filter inefficiently stopping dust particles entering into the air mixing cabinet. Dusted motor at this time 4. Recommend disposable Merv eight filters are used and swapped out every 1 to 3 months to keep system cleanly and reduce dust build up. At this time homeowner would like indoor search protector installed to protect the brains of the system and would like a outdoor search protector installed in the summertime. Would also like
Performed Diagnostic On thermostat. Upon arrival client stated that system is not remembering set temperatures and keeps resetting even after clearing the previous 62Â°. Thermostat was replaced with Sensi And Wi-Fi was left off. Thermostat was tested and is fully operational and heating and cooling. Upon departure system is fully operational and thermostat is no longer resetting
Arrived on site. Started tune up of ac system. Cleaned condenser coils, flushed out drain lines. Inspected electrical. Refrigerant charge is good. Filter is okay. Changed out blower cap under parts warranty. Unit is cooling upon departure.
Performed diagnostic on system. Unit is not cooling. Found compressor was not turning on. Found Unit completely flat on r-22 refrigerant. Went over recharge price for refrigerant. Charla decided that itâ€™s not worth fixing and they will be replacing the unit. They purchase their systems through Ferguson and have fire and ice replace it. Helped put a portable AC unit in that they had on site. System is not operational upon departure, left power to unit off.
Performed furnace tune up on a 2017 goodman. System has a 46 degree temp rise. Combustion blower and main blower motor are functioning well and amperages are in range. Hot surface ignitor is reading in range. The system has a merv cabinet with a merv 11 filter that needs to be replaced. Single secondary motor is within range however it is leaking its lubrication out of the top which is the first sign of failure. Flame sensor was cleaned and reinstalled. Duct runs are tight and free of any rips or obstruction.
Arrived on site to diagnose a 2017 Goodman system that is not cooling. Condenser located in back yard. Furnace and evaporator coil located in attic. Spoke over with client and she stated unit dose not turn on or cool. She tuned system on and was not operational. Went and inspected both indoor and out door units. Found no voltage on either units advise had to trouble shoot for power advised tenants. Checked all electrical wiring and connection were good went and checked breakers and found Furnace breaker fused tripped. Identified on breaker switches which is to furnace and Ac. Switched it back on and now had system operational and cooling. Had system run for 10 mins to ensure breaker would not trip again. Recommend adding surge protectors to unit to prevents from having shortage issues. Spring tune up Inspected indoor unit. Found few ducting used and good condition. Filter was ok as it was just replaced 3 months ago. Checked all electrical wiring, connections, circuit board, and com
Performance tuneup on the condenser
Air conditioning maintenance in Anaheim, Ca on an American Standard System.
2 system maintenance in Anahiem
Do you single system air conditioner and heater maintenance out here in Anaheim
Heating maintenance in Anaheim