Upon arrival Perfromed diag. Found system to be on high head pressure. Found secondary motor control to be out of range, does not get fan running, compressor was still operational. Reset switch added new control and system is runn8ng and cooling. Condenser fan motor is in really bad condition. Leaking excessive oil. Ordering motor from Lennox.