Luis was great! He was very thorough. I am very happy with his services!
Very nice experience. No pressure great guy.
Performed a heating maintenance on a 2016 Goodman system. Cleaned and Adjust Burners. Check Combustion Air for Proper Venting. Examine the Heat Exchanger for Damage / Corrosion. Test Furnace Safety Controls. Inspect Gas Piping. Tighten Electrical Connections. Measure the Voltage and Amperage. Flush the Condensate Drains. Measure Tempurature Difference between Supply and Return Air. Vacuum Furnace Return Grille. Adjust Gas Pressure & Pilot. Clean in-place Blower Compartment. Inspect Blower Wheel for Proper Balance. Check the System's Static Pressures to Ensure Proper Airflow. Inspect Duct Connections for Air Leaks / Sizing / Insulation. Check all System Safety and Limit Switches. Clean Flame Sensor. Inspect Carbon Monoxide Detector. Check Thermostat for Proper Operation / Calibration. Filter was changed out. System was fully operational at time of departure.
Arrived on site to install parts
Upon arrival client said a company did drain line repairs and it didnâ€™t fix the issue. Inspection found the primary pan of the evaporator coil had cracked. Also found evaporator coil leaking refrigerant. Found issues with the condenser. Condenser fan motor is leaking oil and over amping. Capacitor is also low. Need to replace those as well. Advised client of issues and they moved forward with the install. Advised client to not use system until its repaired on Monday.
Client stated no cooling -System was not operational upon arrival -Fan motor and secondary motor control needed to be replaced -The starter was also in rough condition -Fan motor, smc, and start were all replaced -Condenser has a full electrical rebuild -System is operating properly, motors are not drawing too much power -Refrigerant levels are within range -Client is aware these repairs are not going to make the system bulletproof -System is cooling
Upon arrival performed maintenance on cooling system. Outdoor system opened up and cleaned entirely. Secondary motor control is in range. Hardstart on compressor is beginning to climb due to age. Primary starter has small pitting where contacts meet. Performed blower wheel cleaning. Advised moving over to upgraded filtration will Benefit system by keeping it as clean as possible. Ducting is in good condition. Put system back together. System is operational upon completion.
Upon arrival performed replacement of high limit switch. System is operational upon departure.
Upon arrival performed heating tuneup. Indoor motor is good and in range. Borrower is beginning to get dust buildup. Circuitboard and electrical connections are good. Amperages through our system or in range and efficient. Wiped and wax entire furnace cabinet. Damaged switch and blower will orderFrom Goodman tomorrow morning client would like to visit next week because he is only available next week. Static pressures throughout system are in very good condition. Ducting is nice and strapped. Gas valve in working order flame sensor cleaned. System reset tested and fully functional for departure.
Thermostat was blank. Ceiling saver switch was tripped and inoperable causing a block in the low voltage circuit. Installed new safety switch and cycled system.
Goodman Ac maintenance in Chino Hills, Ca.
Performed routine spring maintenance on trane unit. Installed safety switch
Furnace maintenance in Chino
Fall Maintenance 1/2/2019
Doing a single system air conditioner maintenance out here in Chino