Upon arrival performed heating tuneup. Indoor motor is good and in range. Borrower is beginning to get dust buildup. Circuitboard and electrical connections are good. Amperages through our system or in range and efficient. Wiped and wax entire furnace cabinet. Damaged switch and blower will orderFrom Goodman tomorrow morning client would like to visit next week because he is only available next week. Static pressures throughout system are in very good condition. Ducting is nice and strapped. Gas valve in working order flame sensor cleaned. System reset tested and fully functional for departure.