Summer AC Maintenance Performed Upon arrival both systems are working and operational. I began my maintenance at the outdoor condenser by breaking it down and cleaning with water and coil solution. Inspected all electrical components for wear and ensuring tight connections, as well as tested system for amp draws. Checked and measured system pressures and charge. Upon inspection of electricals I found there to be no surge protection, recommended to protect electrical components in system. I then proceeded to the indoor furnace unit. Inspected condensates for drainage and safety switches for functionality. Inspected blower compartment for dust and proper balance. Checked electrical for tight connections, inspected electrical components. Upon recommendation members had surge protection installed on both systems. Upon departure systems are working and operational.