Tech arrived on site with new drain pan. Lifted evaporator coil up and disconnect the plenum. Slid old pan out. Installed new drain pan. Connected pvc fittings and added T and trap. Blew out primary and secondary drains as they were restricted. Poured 3 gallons of water into pan to test. Everything was draining properly.