Repaired leaking flare fitting at the outdoor unit. Repaired leak using thread nylog, pressure tested system, vacuumed down to 500 microns. Recharged system 12.13 lbs per specifications. Tested system on cooling and verified leak repair.
Arrived on site to perform diagnostic/warranty. System is not cooling. Indoor unit is blowing air, outdoor unit is not kicking on. Checked outdoor unit electrical and system components. System is recieving power and command but is not turning on. Found low pressure switch tripped, and found unit on Low refrigerant. Found both high and low side fittings loose and oil residue on both lines. Tighten up nuts and bubble tested, no leak present. Recharged system with refrigerant to manufacture spec. System is now producing proper temperature split. System is operational upon departure.
Installation of a Comfort Pro 42,000-60,000BTU Series-X Slimline Condenser and Coil.
Training to serve our customers and our team with EGIA Contractor University at Hotel Del Coronado... Always Learning!