Mr. Pucillo was early for his appointment and had two thermostats installed, checked and set in the time it would have taken me to read the instructions. He is everything I would have wanted as an employee when I was working. I am so glad we are one of your customers. Bill Stanhope
The sales person offered detailed explanations of our needs and the solutions of the new system. The quote was fair and reasonable and offered sound alternatives such as removal of old and failed insulation, sealing the ducts and the reapplication of new insulation and wrap. None of the other quoting firms offered a similar cost saving alternative. The installer also kept us informed at each step of the process, arrived exactly on time and left the site immaculately clean. Great job !!
Tyler is the best . He called before his arrival was very friendly, knowledgeable and professional. After completing the inspection of our HVAC system he explained to us what he did and showed us pictures as well. Very thorough. I trust and respect cool air solutions and their team and would recommend them to anyone. Thank you Tyler for taking great care of us.
Arrived on site to preform ecobee thermostat installation.
Performed a heating maintenance on two Lennox system. Cleaned and Adjust Burners. Check Combustion Air for Proper Venting. Examine the Heat Exchanger for Damage / Corrosion. Test Furnace Safety Controls. Inspect Gas Piping. Tighten Electrical Connections. Measure the Voltage and Amperage. Flush the Condensate Drains. Measure Tempurature Difference between Supply and Return Air. Vacuum Furnace Return Grille. Adjust Gas Pressure & Pilot. Clean in-place Blower Compartment. Inspect Blower Wheel for Proper Balance. Check the System's Static Pressures to Ensure Proper Airflow. Inspect Duct Connections for Air Leaks / Sizing / Insulation. Check all System Safety and Limit Switches. Clean Flame Sensor. Inspect Carbon Monoxide Detector. Check Thermostat for Proper Operation / Calibration. Filters where not changed this visit. Both systemâ€™s where fully operational at time of departure.
Installation of Phenomenal Air R6.0 This estimate has seasonal special pricing of $1620 with an additional 10% military discount as a thank you for your service. With a happy early Veterans Day! Performed FAU maintenance on 2 year old Lennox unit. Cleaned return grate. Filter was recently installed by Juan. Flushed condensate drain with water and verified condensate pump works. Inspected electrical connections. Inspected blower compartment, blower wheel is clean and balanced. Tested resistance of hot surface igniter. Cleaned flame sensor. Temperature rise is within limits. Opened damper to supply more air to the additional bedrooms. Trimmed flue exhaust pipe so cover would sit lower to prevent water from entering. While working on his system I accidentally caused a short which blew the surge protector that the furnace was plugged in to. Because of this and with Daveâ€™s permission I installed a surge protector on the furnace. Items added: Phenomenal Aire 24v transformer
Arrived on site to perform mini split maintenance
Inspected system for faults. Added refrigerant to the system and tightened flares on the kitchen head unit.
Technician arrived to perform spring tune up for Mini Split and 2 Heads -Condenser was cleaned out with water -Electrical components are working good, however client stated condensate pump was making a strange noise on Sunday -The noise is not currently happening, I did open it up and adjust the way it was sitting, as it was a little off center -Refrigerant levels are within range -All four filters were cleaned out -System is cooling efficiently and is ready for summer
Upon arrival found system low on charge. Did a leak inspection on condenser and found it leaking out the service ports. Replaced service ports under warranty. Added charge. System is now cooling properly upon departure.
Arrived on site to perform spring tune up on 2 2004 Goodman units. Client son was home. Cycled both units and son stated one in has been down for 1 Month and wants it fixed for summer. Had to inspect bigger unit. Found start worn out. Secondary motor control is completely bad. Put a new one in to test if unit operational. Compressor turned off but fan motor did not. Advised fan is seized up. Unit would be needed parts replaced or as far as rebuilding unit to get it operational. Was not able to checked pressure but dose hold R-22. Washed condenser coil inside and out. Found starter worn out. Recommend replacing to prolong life. Secondary motor control is good as it has been replaced in past. Fan motor is leaking oil and is pulling max amps of 1.6 and advised motor can fail. Checked start up amps and compressor has high start up but in range recommend adding compressor booster kit due to age and hard start up to preserve compressor life. Run amps is pulling 9 amps and max at 16. Advise
Performed maintenance on a 2019 Lennox ductless mini split. Both head units are heating over 20 degrees. Drains were checked, filter were cleaned. Outdoor unit was deep cleaned. Voltages and amp draws are in range. Outdoor unit is not electrically protected. Both systems were operational at end of appointment.
Performed mini split diagnostic on 2020 Lennox system. Client stated that the other day condensate was not draining out and It had completely flooded over and started Draining down the side of the living room wall. Original condensate pump was no longer functional and not draining pan out. Replaced with new condensate pump and system is fully operational and draining out properly. Labor and parts were covered under warranty
Replace existing furnaces with listed equipment. Adapt existing cooling systems to new furnaces. Add 5â€ Merv 11 filter kits to furnaces along with new plenums. Remove all duct insulation, seal and re-insulate ducting. Seal existing floor cans. Permits and HERS included. After Lennox rebate total $15,501.00. $300 dollar Lennox card sent directly to customer Financing= 90 days no interest/payment default to 120 Months 6.9% interest 0-down $183 per month
Getting a system up and running out here in El Cajon.
AC Only and fix ducting
Checked mini split for proper operation. Cleaned filters and checked drain pumps. Cleaned outdoor coil. Measured voltages and motor amp draws. Tightened electrical wiring. Tested low voltage
Spring maintnenance on condensor In el cajon