Technician arrived on site. Found the upstairs system flat on refrigerant. Got permission to do pressure test leak detection. Was unable to locate the leak. Uv dye was added to the system previously. Used black light and located dye in the evap coil. Ordering coil for warranty. Field supervisor will come out Friday to give estimate on equipment.