Tech arrived on site. Found unit operational but not cooling. Filter was restricted snd condenser was also restricted. Did tune up and cleaned unit. Found the capacitor was weak, causing intermittent issues. Replaced the cap. Once everything was cleaned checked charge. It was good. Unit is operational upon departure. 1 year parts/labor on capacitor.