Upon arrival performed maintenance on 1 yo Lennox system. Opened up outdoor system entirely ran amperage test, cleaned outdoor coils. Coils built up some dust, took all doors off and cleaned coil. System is running efficient. Filter is ready to be replaced, client orders off Amazon and replaces. Circuit board and electrical connections good. UV bulb in working order. Heating order of operations good. System was reset tested and fully functional upon departure.