Returned to perform diagnostic. Homeowner stated system is not operating again. In line fuse on transformer popped. Found short at outdoor unit wire. Outdoor wire needs repair as well as primary motor control is burnt and pitted. Homeowner only wants to take care of whatâ€™s broken for now until she hears back from Edison on the replacement of her system. Will replace parts as they fail until then. Replaced primary motor control and accessible wire from furnace to condenser. Replaced fuse. System is operational upon departure.