Tech arrived on site. Found low voltage wires lose on control board. Corrected wiring and tested in heating and cooling modes. Unit is cooling and staff is happy.
Install Nest Thermostat, Phenomenal Air, Indoor Surge Protector and perform indoor coil cleaning.
Tech arrived on site. Manager wasnâ€™t on site. Had to reschedule the call.
System is operating at what is needed to. System is heating at 119 degrees. Home has very little insulation
Heating maintenance tune up
Air flow adjustmemt to master bedroom