Tech arrived on site to a 9 year old system. Coil was corroding due to the salt in the air. Did not use chemicals on coil. Hosed it down. Cleaned out electrical. Start components are rusting out. Amps were okay. Compressor start amps getting high. Recommend booster kit to lower. Charge and temp split is perfect. Static is good. Customer declined recommend repairs.