He was on time, friendly and show me the photo and give information as how things look and what going on or what can happen after time with the equipment. It was a good relief to know I have a experience technician, for the price I paid. Thank You.
Respectfully, Friendly, Well Information, Help me understands what was going on with my ac nest thermostat and the furnace safety controls when water level is high.
He answered all my question and explain what might had happen with my smart thermostat back in June. He was polite, had his mask on, work was done in a short time. I was very satisfied.
I purchase a new HVAC system through CAS just a little over a week ago. They kept their promise of installing our new system today, 9/24/2020. We are extremely happy with the quality of the using and their installers! Would recommend and already have this company!
Luke. was pleasant to deal with.
Upon arrival performed maintenance on hvac unit. Opened up entire system and washed outdoor coils. Found coils to be pretty dirty. Washed down system. Tested secondary motor control, in range. Refrigerant levels are good. Amperages throughout system in range. Client will purchase in surge and place it on system. Client is purchasing own filters. Dusted off all electrical components, waxed furnace unit. Condensation pump in working order, system was reset tested and fully functional upon departure.
Tech arrived on site. Found the batteries to the thermostat to have failed. Replaced them and the unit began to cool. Found the outdoor capacitor to be weak. Replaced it. Found no secondary drain protection on the unit. Installed new safety switch. Cleaned outdoor unit coils. Replaced filter for indoor unit. The indoor unit is covered in dirt. Cleaned out electrical compartment. Heavy cleaning will be required on fall visit. Unit is operational upon departure.
Performed AC maintenance on a Lennox system. Units cooling temperature split is 20 degrees. Condensate line is clear and pump is in good working condition. Indoor blower is clean and in range. Primary start control is in range at thus time. Outdoor unit was dirty and chemically washed. Compressor and fan amps are in range at this time. Refrigerant levels are ok. Outdoor unit is not protected. Electrical components have minor signs of wear. System was running upon end of appointment.
Upon arrival performed diagnostic on 2 year old system. There was a some water in saftey switch? Checked primary there is no clog, water pump is in working order. System is operational upon departure.
Performed routine fall maintenance on Trane furnace in lakeside. Checked air filter and was clean. Verified correct operation of system, system is operating correctly at this time with no recommendations on this visit.
After opening access to the duct work found that the ducting was in very bad shape and in need to replacement. We can install dampers into the existing ductwork but the ducting will be damaged as areas are very hard to access and the ducting is already falling apart. After having our install manager do a job walk found that by redesigning the duct system and also adding a second register in the upstairs will help to fix the heat load issues upstairs. This estimate includes replacing 7 duct runs and adding an 8th to the upstairs. The install will also include 4 dampers to divert the air on the 4 main duct runs where needed.
Inspected system for faults. Found defective contactor at the outdoor condenser failing to send voltage to the compressor and outdoor fan motor. Replaced the component and tested equipment. Measured starting load amps and voltages. Verified system refrigerant pressures, Filter is clean.
Customer will receive 10% off via lowes using credit card bringing total project cost down to 13836.75 plus $335 back from Lennox (rebate)
Performed AC maintenance on one year old Lennox condensing unit
Performed Routine Fall Maintenance on Lennox Furnace. Inspected duct work and electrical components replaced 16x25x5 merv 11 air filter