I purchase a new HVAC system through CAS just a little over a week ago. They kept their promise of installing our new system today, 9/24/2020. We are extremely happy with the quality of the using and their installers! Would recommend and already have this company!
Luke. was pleasant to deal with.
After opening access to the duct work found that the ducting was in very bad shape and in need to replacement. We can install dampers into the existing ductwork but the ducting will be damaged as areas are very hard to access and the ducting is already falling apart. After having our install manager do a job walk found that by redesigning the duct system and also adding a second register in the upstairs will help to fix the heat load issues upstairs. This estimate includes replacing 7 duct runs and adding an 8th to the upstairs. The install will also include 4 dampers to divert the air on the 4 main duct runs where needed.
Inspected system for faults. Found defective contactor at the outdoor condenser failing to send voltage to the compressor and outdoor fan motor. Replaced the component and tested equipment. Measured starting load amps and voltages. Verified system refrigerant pressures, Filter is clean.
Customer will receive 10% off via lowes using credit card bringing total project cost down to 13836.75 plus $335 back from Lennox (rebate)
Performed AC maintenance on one year old Lennox condensing unit
Performed Routine Fall Maintenance on Lennox Furnace. Inspected duct work and electrical components replaced 16x25x5 merv 11 air filter