Arrived on site to preform diagnostic on Goodman system. Fan motor that was recently installed last visit is no longer spinning. Open panel and found that wire had fell off. Reattached and fan began spinning. Upon departure system is operational.
Annual spring air conditioner maintenance on Lennox unit here in Long Beach
Furnace maintenance in Long Beach
Doing a single system ac maintenance out here in Long Beach
Air conditioning maintenance in Long Beach
American standard furnace and ac tuneup in Lake Forest
Payne furnace and ac maintenance.
Tuning up a furnace today in Long Beach near the Virginia Country Club