Perform condensate leak repair. Upon my diagnostic client stated that he had just recently noticed the secondary drain line from the top of the house was beginning to leak water when the AC was running. Verified the primary drain line was clogged up at P-trap inside of the attic and also the P-trap under the sink in the bathroom. Inspected the primary pan inside evaporator coil and could not find any signs of cracks. Preformed cut and clear and ran dry nitrogen to clear any restrictions within the primary PVC line. Primed line also and verify that it was draining correctly back to the sink. Recommended that they signed up on a maintenance plan to keep system at standard and prevent this from happening again but he will discuss this with his wife whether or not they would like to renew their membership. Upon departure your drain lines are clear.