Upon arrival perform maintenance on hvac system. Circuit board has burn spots on terminals. Secondary motor controls are both out of range for indoor units. Blower wheels are dirty and need some cleanings. Washed outdoor coils. Condenser fan motors are leaking excessive oil. Secondary outdoor motor controls outside are good. Hardstart kits in working order. Refrigerant levels are in range. 1. Dirty blower wheels 2. Secondary motor controls out of range. 3. Condenser fan motors leaking excessive oil Systems are operational, have a few parts that need attention. Client is aware of how system is operating. Signed client up with ESA CLUB.