Jorge was professional and through!
Cool Air Solutions installed and maintains all of my home HVAC with well trained technicians who also provide great advice and service for keeping my units at maximum efficiency and life expectancy!
I expected a tech that was going to rush through some minimal work & try to up sell us on all kinds of repairs or upgrades. My immediate impression of Travis was that he was so friendly & polite. Then I couldn't believe how much he took apart and took the time to show me and explain what he found. Instead of just rushing through everything he spent over 4 hours inspecting, cleaning & repairing. Then when he finished he tested everything, put it all back together & cleaned up. Travis was great & we hope he'll be the one that returns in 6 months.👍🏻 Bobby & Krista Mission Viejo
Michael checked out the system completely and offered helpful suggestiond to make the system work more efficiently. He's a very friendly and helpful man.
Replacement of upstairs ducting, dining room, and kitchen.
Installation of a 4 Ton XC25 Variable Speed Diamond Package Lennox Visa Gift Card is applicable bringing the total to $17,055 at $197/mo
Performed Ac maintenance on 6 year old Carrier system. Cycled system for cooling. Pulled condenser fan motor and thoroughly washed out condenser coil inside and out with coil cleaner and water. Checked system electrical and components. Amp draws for compressor are within range. Condenser fan motor is close to over amping and has started to leak oil. Secondary motor control is out of range for condenser fan motor, which explains why amp draws are high and motor is leaking. Refrigerant levels are in range and system is producing proper temperature split. Went over findings and recommendations with homeowner. With approval went ahead and replaced secondary motor control. Homeowner had coupon for discounted maintenance promo. Cycled system, system is operational upon departure.
Replace existing equipment with listed equipment. Install new B-Vent exhaust thru the roof. Permits and HERS testing included.
Samsung substitute equipment
Found that 60 amp breaker was not fully seated to lag bar on breaker panel this is giving an incomplete voltage transfer and not turning on the system from the disconnect and to the starter. Breaker must be swapped to further diagnostic on AC condensing system.
Doing a single system heating maintenance.
Blower motor replacement and maintenance in Mission Viejo, Ca.
Lennox blower motor testing in Mission Viejo, Ca.
Ac maintenance in Mission Viejo
Nick Wilson /Mission Viejo
Heating maintenance and filter changes in Mission Viejo