Tech arrived on site. Found 1 hvac system installed in 85. Did EXTENSIVE coil cleaning. Coil is in bad shape. Checked electrical start components. Caps are failing. Both fan motors are over amping. Compressor is being started by the hard start. Charge is okay. Temp split is 15. Customer declined to be quoted for recommended repairs and comfort club.