Tech arrived on site. Found the secondary float had triggered. Float was wired to condenser wires. Causing it to turn on and off. Wired it to break R. Flushed out lines. Unit is cooling at this time. Both uv and air scrubber bulbs had failed on unit. Will replace during fall maintenance of equipment.