Upon arrival performed diagnostic on air conditioning system. Client said breaker was tripping and not blowing cold air. Found secondary motor control to be completely out of range. Replaced and restarted system. Breaker still tripped. Took compressor out of circuit and found compressor was issue. Opened top of condenser and checked terminal blocks on compressor and got 2 leads to ground confirmed. Checked duct working inside of attic and found ducting that is falling apart. Condenser fan motor is leaking oil and has play on shaft. Laura would like to have replacement options, Darren coming out today between 12-2. System is non operational.