Technician arrived on site and found no power to the unit. Found the breaker had been tripped. Checked the motors to see if anything was grounded. Everything checked out. Coils were restricted from dirt. Lack of maintenance is not covered under warranty. Cleaned coils and inside of the condenser with chemicals and water. Unit is operational upon departure.