Tech arrived on site. Found 1 5 ton Goodman system. 11 years old. Cleaned out condenser. Checked electrical. Cap was weak but still within range. Fan motor had been replaced. Charge is good. Temp split is high. Indicating a lack of airflow. Static reflects that. Replaced the cap. Unit is operational upon departure.