Performed maintenance on 9 year old Goodman system. Cycled system for cooling. Checked indoor unit electrical and system components. Filter is clean. Checked outdoor unit electrical and system components. Amp draws for compressor and condenser fan motor are within range. Secondary motor control is in range, was recently replaced. Primary motor control has slight pitting building up at contact points. Removed condenser fan motor and thoroughly washed out condenser coil inside and out. Compressor has a slight hard start turning on. Went over findings and recommendations with homeowner. Also advised that this is the last visit of the membership program and would be time to renew for future maintenances. Homeowner wants to hold off on any work for today and would like to hold off on maintenance program as well. Cycled system, system is operational upon departure.