Tyler was professional, knowledgeable and took time to answer questions and discuss solutions. I was very happy with my experience.
Refrigerant charge and uv dye leak detecting injection in Rancho Santa Fe, Ca.
Lennox system check up in Carlsbad
Drain line issue
Found drainline to be slipped incorrectly due to furnace now being on 4 inch stands. Need to raise furnace and drainline.
Air conditioner diagnostic
Ac condensate trap clearing and safety switch installation in Rancho Santa Fe
Ac assessment in Rancho Santa Fe
Completed a diagnostic on a single system heat pump out here in Rancho Santa Fe.
Ac diagnostic and repair in Rancho Santa Fe