Tyler was professional, knowledgeable and took time to answer questions and discuss solutions. I was very happy with my experience.
Germicidal light and ducting replacement quote
Replaced filter which was considerably restrictive with new merv11 filter. The static pressure dropped dramatically after this. Replaced the high voltage power supply with new whip with a proper earth ground. Relocated the zone board off the top of the furnace and mounted it onto the support truss. Extended the low voltage wiring between the zone board and the furnace circuit board with new wires. Ensured extra wires were grounded to common. Replaced 40VA transformer powering zone board and air scrubber with a 75VA to tolerate the load. Tested system and equipment is operating properly at this time.
Recorded static pressures and supply temperatures for each individual zone. As well as all zones together. Tested heating in minimum and max heat pump and stage 1 and 2 gas heating. All temperatures look okay. Filter is clean. Ordered high limit switch for the furnace to replace under parts warranty. Return to replace high limit switch for indoor furnace
Refrigerant charge and uv dye leak detecting injection in Rancho Santa Fe, Ca.
Lennox system check up in Carlsbad
Drain line issue
Found drainline to be slipped incorrectly due to furnace now being on 4 inch stands. Need to raise furnace and drainline.
Air conditioner diagnostic
Ac condensate trap clearing and safety switch installation in Rancho Santa Fe