Micheal was great ... polite and very knowledgeable... service like his is the reason I use this company !
Upon arrival performed maintenance on air conditioning system. Refrigerant levels in range. Filter was replaced. Secondary motor control is out of range. Client said he needs to speak with his wife about repairs. Indoor blower wheel is dirty. Dusted off all electrical components. Washed outdoor coils with chemicals, coils were extremely dirty. - Recommend adding booster kit to keep amperages low on compressor start up - Seconary motor control is out of range -Washed outdoor coils - refrigerant levels in range.
Preformed AC maintenance on 2020 carrier heatpump
Performed furnace maintenance on 2008 Lennox heater 1. Found that flame sensor has oxidization occurring and could lead to failure of blower start up in heating mode 2. Evaporator coil contain no secondary float switch in case of coil overflowing and water damage 3. Blower wheel assembly is very dirty and covered and debris 4. Found cracked washer on heat exchanger, washer is used for stabilization when She change it expands and contracts this needs to be watched closely and examined every year for cracks
Ac maintenance and cleaning
Total system rejuvenation in Redlands.
Performing much needed maintenance on Heil A/C and furnace in Redlands