Performed diagnostic on 2014 system. System is leaking water on to ceiling. Found a crack in main drain pan at the primary connection port. Because this is part of the drain pan, the whole pan has to get replaced. Can not replace pan without pulling off evaporator coil. Evaporator coil will have to be unwelded and refrigerant would need to be pumped down. Andrew will be quoting and emailing customer a estimate. Emailing information over to Andrew.