Excellent work. Great workmen
Performed AC diagnostic on eight-year-old carrier condensing unit. During my diagnostic I found that the secondary motor control had been bad on the fan and hermetic terminals. This component was then replaced and the compressor amperage is pulling 8.1 amps along with fan pulling a 0.8 amps. Found traces of oil leaking off condenser fan motor And pitting occurring on high voltage relay. Upon my departure system has 15Â° split And appears to be functioning and cooling.
Doing a two system ac and furnace maintenance out here in San Juan Capistrano.
Circuit board replacement under warranty
Day 3 of install
day 2 of install
Doing a single Bryant system put here in San Jaun Capistrano
Doing a full system rejuvenation out here in San Juan Capistrano