Excellent work. Great workmen
Performed Heating maintenance on a pair of Lennox furnaces. Both systems are equipped with icomfort white series thermostats that are functioning well at this time. Heating temperature splits are within range at 30 and 45 degrees. Condensate lines are clear, duct runs are sealed. Electrical amp readings are in range and recorded. Gas valves are operating within spec. Homeowner has Tesla installed surge protection on 1 entire system. Customer wants to install surge furnace protection on his own. Both systems were operational at end of appointment.
Replaced ECM condenser fan motor under warranty. Installed surge protection on condenser.
Preformed furnace/maintenance On two system Lennox. Upon my maintenance XC20 fan motor Was intermittently working and not running at the proper capacity. Determine that fan motor is going bad and will order new one under warranty although labor warranty is expired. Also found that system is not equipped with surge protection on both indoor and outdoor units. Discussed That surge protector should at least be put on outdoor unit to protect ECM motors and compressor to increase longevity of AC systems. Performed maintenance on AC systems and cleaned off condenser coilâ€™s and checked refrigerant pressures. All components on AC system besides fan motor checked out. Performed maintenance on furnaces and double checked temperature rise along with secured all gas fittings and ensured no gas leaks. Filters are both replace due to cat hair buildup. Recommended that indoor air quality upgrade with whole house purifier that can be installed to increase the life of the system and reduce dust build
Performed furnace maintenance on 2 9 year old carrier units. Cycled systems for heat. Verified proper heating sequence of operations. Cleaned furnace, blower assembly and heating compartment. Ran systems through 20 point inspection checklist. Went over all concerns and recommendations with homeowner. Homeowner is fully aware of the condition of his systems. Wants to hold off on any repairs for now. Cycled system, system is operational upon departure.
Performed AC diagnostic on eight-year-old carrier condensing unit. During my diagnostic I found that the secondary motor control had been bad on the fan and hermetic terminals. This component was then replaced and the compressor amperage is pulling 8.1 amps along with fan pulling a 0.8 amps. Found traces of oil leaking off condenser fan motor And pitting occurring on high voltage relay. Upon my departure system has 15Â° split And appears to be functioning and cooling.
Doing a two system ac and furnace maintenance out here in San Juan Capistrano.
Circuit board replacement under warranty
Day 3 of install
day 2 of install
Doing a single Bryant system put here in San Jaun Capistrano
Doing a full system rejuvenation out here in San Juan Capistrano